Installing a Radiant Barrier in your attic is like putting your home under an umbrella. We all know our attics get hot almost year round in the South. This happens due to the radiant heat of the sun being transmitted thru the roof and attic insulation because there is nothing to stop it. Radiant barriers won’t allow the radiant heat to pass thru. As you consider radiant barriers, remember at least one side most be to an air space. Barriers can work be either reflecting or not releasing radiant heat or both.
You are likely already using radiant barriers in your home. Most HVAC duct systems use a radiant barrier on the outside of the insulation in the attic. That duct work is only R-4 to R-8 yet it still manages to deliver cold air to your house, that is only possible with the radiant barrier exterior. As a tip, keep that duct work clean. Any loose insulation or cardboard boxes on or against the surface negates its effect and will transmit more heat into the duct work. I do believe in buried duct work, but it must have sufficient insulation (but this is a different topic).
Radiant Barrier can be a DIY job for smaller spaces, but I recommend a Pro. There are many tricks to the trade and the more hands available the easier to install these products.
From Building America Solution Center
A radiant barrier is typically a layer of aluminum foil-reflecting material placed in the attic next to an air space to block radiant heat transfer between a heat-radiating surface (such as a hot roof) and a heat-absorbing surface (such as conventional attic insulation). Figure 1 illustrates the locations in which a radiant barrier may be installed in an attic. Only locations 1 and 2 are recommended for sheet radiant barriers because dust will accumulate on the radiant barrier if it is installed at location 3. Other types of radiant barriers, “chips”, foil faced air bubble-packing and multi-layer products, are acceptable for location 3 (more below).
Figure 1. There are three potential locations for an attic radiant barrier – adhered to the underside of the roof decking, hanging from the rafters, or on the ceiling insulation.
Aluminum foil, the operative material in attic radiant barriers, has three physical properties of interest here. First, it reflects thermal (long-wave infrared) radiation very well. Second, it emits (gives off) very little heat. Third, its vapor permeability is very low.
Two things affect the performance of a radiant barrier system: the level of insulation in the attic and the geographic location of the home. A radiant barrier system can reduce the heat flow into the house from the attic by approximately 40%. This does not mean a radiant barrier will reduce the homes’ energy use by 40%, as many advertisers claim. This means that the portion of the cooling load represented by the attic is reduced by 40%, which typically equates to 8% to 12% of the annual cooling costs.
Further clouding the savings question is the impact of attic insulation levels and geographic location. Attic insulation levels have a large impact on the amount of heat flow that is reduced by 40%; in other words, if you have little or no insulation in your attic, a 40% reduction is very significant, but if your attic is insulated to R-30 or better, there is very little heat flow to reduce. However, if the HVAC duct work is in the attic, a radiant barrier keeps it cooler during the summer. In climates where summer heat gain from the attic is minimal, the advantages of a radiant barrier diminish.
Four generic types of radiant barrier are most common:
- Foil products: these products are available perforated (vapor permeable) and unperforated (vapor retarder). These products are available as single-sided or double-sided foils with another material as backing, such as craft paper, mylar, or polypropylene. Some products are further strengthened by fiber webbing sandwiched between the foil and the backing. The strength of the backing material is important since unreinforced foil tears very easily. In an attic ceiling or roof deck application (locations 1 and 2 in Figure 1) there is no significant performance difference found between single-sided foil and double-sided foil. The first layer of foil will reduce radiant heat gain by at least 90%, making the reduction provided by the second layer of foil insignificant.
- Foil-faced roof sheathing materials (decking): these product come from the manufacturer with a foil facing adhered to one side of the sheathing. The main difference between these products is if and how the laminated foil surface is perforated. Some products laminate a non-perforated radiant barrier, some products laminate perforated radiant barrier, and some products perforate the product after the foil is laminated to the decking, penetrating the foil, glue, and substrate. The perforations are intended to allow the decking to “breath” allowing the passage of moisture. The efficacy of the decking’s ability to pass moisture is more important in humid climates.
- Radiant barrier “chips”: unlike sheet-type radiant barriers, these “chips” are blown onto the floor of the attic — typically to a depth of 3 or more inches and act as a multi-layer product with many “trapped” air pockets. These air pockets cause this product to function somewhat like traditional fibrous insulation products. Even though this product may collect dust on its uppermost layer, the remaining layers and air spaces work to significantly reduce heat transfer through the ceiling assembly.
- Foil-faced insulation: These products are best deployed as wall insulation. Foil-faced insulation products should not be installed at the roof deck unless the attic is sealed construction. If the attic space is vented, the thermal insulation will be separated from the attics’ air barrier, typically located at the interior ceiling drywall. Due to this, foil-faced insulations installed at the roof plane of a vented attic will not derive any advantage from their R-value. They will still preform as a radiant barrier; however they are more costly than single- and double-sided foil products. The insulating material may be
- polyethylene “air-bubble” packing
- multilayered foil systems.
How to install a Roof Truss-Mounted Single- or Double-Sided Foil Radiant Barrier in an Existing House (retrofit):
Figure 2. Radiant barrier sheeting can be stapled to the underside of the rafters or along the inside edge of the rafters.
In attics, single-sided radiant barrier material should be installed with the foil side facing down.
The radiant barrier acts as a barrier against radiated, not convected, heat so there is no need to cut off air flow in the attic. In fact, to facilitate attic ventilation under a radiant barrier attached to the rafters, a gap should be left at the soffit and at the ridge. Small tears and holes will not significantly lessen the performance of the radiant barrier, so don’t worry if you must cut and patch around obstructions such as vent stacks and truss supports.
To install a foil radiant barrier in an existing attic, staple the foil material to the underside of the top chord of the roof trusses or to the underside of the roof decking (Figure 1). The air space above the radiant barrier is not critical to the system’s performance, so attaching directly to the underside of the decking is acceptable. An air space can be provided by allowing the radiant barrier to sag, as illustrated in the circled “Alternative Method” shown in Figure 1 above; this will allow the roof decking and shingles to be slightly cooler during the day.
How to Install a Radiant Barrier in an Existing Home
This work should be done with two people, for ease as well as safety.
- Measure the length of the attic roof from peak to soffit.
- Return to a stable surface to measure and cut the radiant barrier material to size. The material usually comes in rolls of 50 to several hundred feet. It’s easiest to cut and reroll all the lengths you’ll need before returning to the attic.
- Take pre-cut radiant barrier material back to the attic.
- Starting at one end of the attic, place the plywood or 1×12 as a stable surface across two of the attic truss members. Try to minimize compression of existing insulation. Provide one work platform at the peak and one at the soffit end so that both installers can work together. Safety reminder: Be extremely careful at the sides of your support surface. If you step on an edge, the surface can tilt and drop you through the ceiling drywall below.
- Unroll one length of the radiant barrier material from soffit to peak.
- Leaving one or two inches of free space at the roof peak to allow attic ridge-vent ventilation, staple one corner of the material to the underside of the top chord of the first roof truss.
- Continue stapling the edge of the radiant barrier material down the truss at 6- to 12-inch intervals, stopping 2 to 3 inches above the ceiling insulation to facilitate attic ventilation via the soffit vents.
- Next, staple the other edge of the material to the underside of the adjacent roof truss.
- Continue the process at adjoining trusses until the underside of the roof is no longer visible except for a one- or two-inch strip at the roof peak.
As an alternative, you may staple the radiant barrier material to the underside of the roof decking, adjacent to the top chord of the truss. The air space above the radiant barrier is not critical to the system’s performance, so attaching directly to the underside of the decking is acceptable. If an air space is provided above the radiant barrier, as illustrated, the roof decking and shingles will be slightly cooler during the day.
Figure 3. This finished retrofit installation of radiant barrier in attic shows the air spaces at the soffit and ridge to promote attic ventilation.
It is not very easy to work in any attic, even one with a steep pitch. Always keep in mind that a misstep could be disastrous, since most attic “floors” are not floors at all, but rather 2x4s holding ceiling drywall topped by conventional insulation. You should consider safety first (see installation safety tips listed below).
Take care to avoid compressing existing insulation in the attic.
How to install an Attic Radiant Barrier in New Construction:
There are four widely accepted methods of installing attic radiant barrier systems in new construction:
Method 1 – Install foil-faced radiant sheathing. Perhaps the easiest way to install a radiant barrier in a new house is to use one of the foil-faced roof sheathing materials on the market (Figure 5-“Method 3” and Figure 4).
- The main difference between these products is if and how the laminated foil surface is perforated. Some products laminate a non-perforated radiant barrier, some products laminate perforated radiant barrier, and some products perforate the product after the foil is laminated to the decking, penetrating the foil, glue and substrate. The perforations are intended to allow the decking to “breath,” allowing the passage of moisture. The efficacy of the decking’s’ ability to pass moisture is more important in humid climates as the potential for moisture damage is more severe.
- The price increase for products should be minimal compared to nonradiant sheathing, and the installation does not differ from regular decking, except for a little additional care in the handling of the product.
Figure 4. Roof decking has adhered radiant barrier that is perforated, in addition to the nail holes (image courtesy of Florida Solar Energy Center).
Method 2 – Attach the radiant barrier to the roof decking before it is installed on the trusses (Figure 5 – “Method 3”).
- The decking must be handled carefully to avoid damaging the radiant barrier, often involving flipping the decking over on the roof.
Method 3 – Attach the radiant barrier to the roof deck or truss chords after the roof decking is installed, but prior to the installation of the ceiling drywall (Figure 5, “Method 1 or 2”). The radiant barrier could be a sheet product or a low-emittance paint, also known as an interior radiation control coating that is roller or sprayer applied.
Method 4 – Drape foil across the trusses prior to installing the decking on the roof (Figure 5-“Method 2”).
- Although quick, this approach is fraught with potential disasters; a small breeze at an inappropriate time can wreak havoc with the job. It also effectively hides the trusses as seen from above, possibly interfering with decking nailing.
Figure 5. Three locations and methods for installing a roof deck radiant barrier in new construction.